If you need support or if you would like to share feature ideas or if you simply want to discuss technical aspects around the topic device integration: This is the perfect place.
Welcome to the CodeWrighths Integration Community.
I recently downloaded and installed HART CommDTM (FDT1.2) version 1.0.58. After updating my device catalog in PACTware, I see the new DTM version 1.0.58 / 2019-3-20.
I connected PACTware to my VEGASCAN 693 and did an instrument search (similar to a Topology Scan). When it finds my device, it will search through every HART protocol DTM in my catalog for a matching DTM. When it gets to the CodeWrights HART CommDTM, I get the error:
“could not parse DTM info list”
“Error parsing ‘2019-3-20’ as date datatype”
I believe this is because the CodeWrights HART CommDTM (FDT1.2) version 1.0.58 / 2019-3-20 has the date formatted incorrectly. All other DTMs use a date format of YYYY-MM-DD, but version 1.0.58 has a date string of “2019-3-20”.
If I downgrade to version 1.0.51 / 2014-10-23, the problem does not occur.
This topic was modified 5 months ago by Rory Piper.